<?xml version="1.0" encoding="UTF-8"?>
<zabbix_export>
    <version>3.4</version>
    <date>2018-08-17T16:48:20Z</date>
    <groups>
        <group>
            <name>UPS</name>
        </group>
    </groups>
    <templates>
        <template>
            <template>Template APC Smart-UPS</template>
            <name>Template APC Smart-UPS</name>
            <description/>
            <groups>
                <group>
                    <name>UPS</name>
                </group>
            </groups>
            <applications>
                <application>
                    <name>Battery</name>
                </application>
                <application>
                    <name>Diagnostics</name>
                </application>
                <application>
                    <name>Info</name>
                </application>
                <application>
                    <name>Input</name>
                </application>
                <application>
                    <name>Output</name>
                </application>
                <application>
                    <name>Test</name>
                </application>
            </applications>
            <items>
                <item>
                    <name>APC Battery Capacity</name>
                    <type>1</type>
                    <snmp_community>public</snmp_community>
                    <snmp_oid>.1.3.6.1.4.1.318.1.1.1.2.2.1.0</snmp_oid>
                    <key>apc_battery.capacity</key>
                    <delay>30s</delay>
                    <history>90d</history>
                    <trends>365d</trends>
                    <status>0</status>
                    <value_type>3</value_type>
                    <allowed_hosts/>
                    <units>%</units>
                    <snmpv3_contextname/>
                    <snmpv3_securityname/>
                    <snmpv3_securitylevel>0</snmpv3_securitylevel>
                    <snmpv3_authprotocol>0</snmpv3_authprotocol>
                    <snmpv3_authpassphrase/>
                    <snmpv3_privprotocol>0</snmpv3_privprotocol>
                    <snmpv3_privpassphrase/>
                    <params/>
                    <ipmi_sensor/>
                    <authtype>0</authtype>
                    <username/>
                    <password/>
                    <publickey/>
                    <privatekey/>
                    <port/>
                    <description/>
                    <inventory_link>0</inventory_link>
                    <applications>
                        <application>
                            <name>Battery</name>
                        </application>
                    </applications>
                    <valuemap/>
                    <logtimefmt/>
                    <preprocessing/>
                    <jmx_endpoint/>
                    <master_item/>
                </item>
                <item>
                    <name>APC Battery Replace Indicator</name>
                    <type>1</type>
                    <snmp_community>public</snmp_community>
                    <snmp_oid>.1.3.6.1.4.1.318.1.1.1.2.2.4.0</snmp_oid>
                    <key>apc_battery.replaceIndicator</key>
                    <delay>30s</delay>
                    <history>90d</history>
                    <trends>365d</trends>
                    <status>0</status>
                    <value_type>3</value_type>
                    <allowed_hosts/>
                    <units/>
                    <snmpv3_contextname/>
                    <snmpv3_securityname/>
                    <snmpv3_securitylevel>0</snmpv3_securitylevel>
                    <snmpv3_authprotocol>0</snmpv3_authprotocol>
                    <snmpv3_authpassphrase/>
                    <snmpv3_privprotocol>0</snmpv3_privprotocol>
                    <snmpv3_privpassphrase/>
                    <params/>
                    <ipmi_sensor/>
                    <authtype>0</authtype>
                    <username/>
                    <password/>
                    <publickey/>
                    <privatekey/>
                    <port/>
                    <description/>
                    <inventory_link>0</inventory_link>
                    <applications>
                        <application>
                            <name>Battery</name>
                        </application>
                    </applications>
                    <valuemap>
                        <name>APC Battery Replacement Indicator</name>
                    </valuemap>
                    <logtimefmt/>
                    <preprocessing/>
                    <jmx_endpoint/>
                    <master_item/>
                </item>
                <item>
                    <name>APC Battery Status</name>
                    <type>1</type>
                    <snmp_community>public</snmp_community>
                    <snmp_oid>.1.3.6.1.4.1.318.1.1.1.2.1.1.0</snmp_oid>
                    <key>apc_battery.status</key>
                    <delay>30s</delay>
                    <history>90d</history>
                    <trends>365d</trends>
                    <status>0</status>
                    <value_type>3</value_type>
                    <allowed_hosts/>
                    <units/>
                    <snmpv3_contextname/>
                    <snmpv3_securityname/>
                    <snmpv3_securitylevel>0</snmpv3_securitylevel>
                    <snmpv3_authprotocol>0</snmpv3_authprotocol>
                    <snmpv3_authpassphrase/>
                    <snmpv3_privprotocol>0</snmpv3_privprotocol>
                    <snmpv3_privpassphrase/>
                    <params/>
                    <ipmi_sensor/>
                    <authtype>0</authtype>
                    <username/>
                    <password/>
                    <publickey/>
                    <privatekey/>
                    <port/>
                    <description/>
                    <inventory_link>0</inventory_link>
                    <applications>
                        <application>
                            <name>Battery</name>
                        </application>
                    </applications>
                    <valuemap>
                        <name>APC Battery Status</name>
                    </valuemap>
                    <logtimefmt/>
                    <preprocessing/>
                    <jmx_endpoint/>
                    <master_item/>
                </item>
                <item>
                    <name>APC Battery Temperature</name>
                    <type>1</type>
                    <snmp_community>public</snmp_community>
                    <snmp_oid>.1.3.6.1.4.1.318.1.1.1.2.2.2.0</snmp_oid>
                    <key>apc_battery.temperature</key>
                    <delay>30s</delay>
                    <history>90d</history>
                    <trends>365d</trends>
                    <status>0</status>
                    <value_type>3</value_type>
                    <allowed_hosts/>
                    <units>°C</units>
                    <snmpv3_contextname/>
                    <snmpv3_securityname/>
                    <snmpv3_securitylevel>0</snmpv3_securitylevel>
                    <snmpv3_authprotocol>0</snmpv3_authprotocol>
                    <snmpv3_authpassphrase/>
                    <snmpv3_privprotocol>0</snmpv3_privprotocol>
                    <snmpv3_privpassphrase/>
                    <params/>
                    <ipmi_sensor/>
                    <authtype>0</authtype>
                    <username/>
                    <password/>
                    <publickey/>
                    <privatekey/>
                    <port/>
                    <description/>
                    <inventory_link>0</inventory_link>
                    <applications>
                        <application>
                            <name>Battery</name>
                        </application>
                    </applications>
                    <valuemap/>
                    <logtimefmt/>
                    <preprocessing/>
                    <jmx_endpoint/>
                    <master_item/>
                </item>
                <item>
                    <name>APC Time on Battery</name>
                    <type>1</type>
                    <snmp_community>public</snmp_community>
                    <snmp_oid>.1.3.6.1.4.1.318.1.1.1.2.1.2.0</snmp_oid>
                    <key>apc_battery.time</key>
                    <delay>30s</delay>
                    <history>90d</history>
                    <trends>365d</trends>
                    <status>0</status>
                    <value_type>0</value_type>
                    <allowed_hosts/>
                    <units>uptime</units>
                    <snmpv3_contextname/>
                    <snmpv3_securityname/>
                    <snmpv3_securitylevel>0</snmpv3_securitylevel>
                    <snmpv3_authprotocol>0</snmpv3_authprotocol>
                    <snmpv3_authpassphrase/>
                    <snmpv3_privprotocol>0</snmpv3_privprotocol>
                    <snmpv3_privpassphrase/>
                    <params/>
                    <ipmi_sensor/>
                    <authtype>0</authtype>
                    <username/>
                    <password/>
                    <publickey/>
                    <privatekey/>
                    <port/>
                    <description/>
                    <inventory_link>0</inventory_link>
                    <applications>
                        <application>
                            <name>Battery</name>
                        </application>
                    </applications>
                    <valuemap/>
                    <logtimefmt/>
                    <preprocessing>
                        <step>
                            <type>1</type>
                            <params>0.01</params>
                        </step>
                    </preprocessing>
                    <jmx_endpoint/>
                    <master_item/>
                </item>
                <item>
                    <name>APC Time on Battery remaining</name>
                    <type>1</type>
                    <snmp_community>public</snmp_community>
                    <snmp_oid>.1.3.6.1.4.1.318.1.1.1.2.2.3.0</snmp_oid>
                    <key>apc_battery.time.remaining</key>
                    <delay>30s</delay>
                    <history>90d</history>
                    <trends>365d</trends>
                    <status>0</status>
                    <value_type>0</value_type>
                    <allowed_hosts/>
                    <units>s</units>
                    <snmpv3_contextname/>
                    <snmpv3_securityname/>
                    <snmpv3_securitylevel>0</snmpv3_securitylevel>
                    <snmpv3_authprotocol>0</snmpv3_authprotocol>
                    <snmpv3_authpassphrase/>
                    <snmpv3_privprotocol>0</snmpv3_privprotocol>
                    <snmpv3_privpassphrase/>
                    <params/>
                    <ipmi_sensor/>
                    <authtype>0</authtype>
                    <username/>
                    <password/>
                    <publickey/>
                    <privatekey/>
                    <port/>
                    <description/>
                    <inventory_link>0</inventory_link>
                    <applications>
                        <application>
                            <name>Battery</name>
                        </application>
                    </applications>
                    <valuemap/>
                    <logtimefmt/>
                    <preprocessing>
                        <step>
                            <type>1</type>
                            <params>0.01</params>
                        </step>
                    </preprocessing>
                    <jmx_endpoint/>
                    <master_item/>
                </item>
                <item>
                    <name>APC Battery Voltage</name>
                    <type>1</type>
                    <snmp_community>public</snmp_community>
                    <snmp_oid>.1.3.6.1.4.1.318.1.1.1.2.2.8.0</snmp_oid>
                    <key>apc_battery.voltage</key>
                    <delay>30s</delay>
                    <history>90d</history>
                    <trends>365d</trends>
                    <status>0</status>
                    <value_type>3</value_type>
                    <allowed_hosts/>
                    <units>Volts</units>
                    <snmpv3_contextname/>
                    <snmpv3_securityname/>
                    <snmpv3_securitylevel>0</snmpv3_securitylevel>
                    <snmpv3_authprotocol>0</snmpv3_authprotocol>
                    <snmpv3_authpassphrase/>
                    <snmpv3_privprotocol>0</snmpv3_privprotocol>
                    <snmpv3_privpassphrase/>
                    <params/>
                    <ipmi_sensor/>
                    <authtype>0</authtype>
                    <username/>
                    <password/>
                    <publickey/>
                    <privatekey/>
                    <port/>
                    <description/>
                    <inventory_link>0</inventory_link>
                    <applications>
                        <application>
                            <name>Battery</name>
                        </application>
                    </applications>
                    <valuemap/>
                    <logtimefmt/>
                    <preprocessing/>
                    <jmx_endpoint/>
                    <master_item/>
                </item>
                <item>
                    <name>Test Last Diagnostics Date</name>
                    <type>1</type>
                    <snmp_community>public</snmp_community>
                    <snmp_oid>.1.3.6.1.4.1.318.1.1.1.7.2.4.0</snmp_oid>
                    <key>apc_diagnostics.testDate</key>
                    <delay>30s</delay>
                    <history>90d</history>
                    <trends>0</trends>
                    <status>0</status>
                    <value_type>1</value_type>
                    <allowed_hosts/>
                    <units/>
                    <snmpv3_contextname/>
                    <snmpv3_securityname/>
                    <snmpv3_securitylevel>0</snmpv3_securitylevel>
                    <snmpv3_authprotocol>0</snmpv3_authprotocol>
                    <snmpv3_authpassphrase/>
                    <snmpv3_privprotocol>0</snmpv3_privprotocol>
                    <snmpv3_privpassphrase/>
                    <params/>
                    <ipmi_sensor/>
                    <authtype>0</authtype>
                    <username/>
                    <password/>
                    <publickey/>
                    <privatekey/>
                    <port/>
                    <description/>
                    <inventory_link>0</inventory_link>
                    <applications>
                        <application>
                            <name>Diagnostics</name>
                        </application>
                    </applications>
                    <valuemap/>
                    <logtimefmt/>
                    <preprocessing/>
                    <jmx_endpoint/>
                    <master_item/>
                </item>
                <item>
                    <name>Test Last Diagnostics Results</name>
                    <type>1</type>
                    <snmp_community>public</snmp_community>
                    <snmp_oid>.1.3.6.1.4.1.318.1.1.1.7.2.3.0</snmp_oid>
                    <key>apc_diagnostics.testResults</key>
                    <delay>30s</delay>
                    <history>90d</history>
                    <trends>365d</trends>
                    <status>0</status>
                    <value_type>3</value_type>
                    <allowed_hosts/>
                    <units/>
                    <snmpv3_contextname/>
                    <snmpv3_securityname/>
                    <snmpv3_securitylevel>0</snmpv3_securitylevel>
                    <snmpv3_authprotocol>0</snmpv3_authprotocol>
                    <snmpv3_authpassphrase/>
                    <snmpv3_privprotocol>0</snmpv3_privprotocol>
                    <snmpv3_privpassphrase/>
                    <params/>
                    <ipmi_sensor/>
                    <authtype>0</authtype>
                    <username/>
                    <password/>
                    <publickey/>
                    <privatekey/>
                    <port/>
                    <description/>
                    <inventory_link>0</inventory_link>
                    <applications>
                        <application>
                            <name>Diagnostics</name>
                        </application>
                    </applications>
                    <valuemap>
                        <name>APC Diagnostic Result</name>
                    </valuemap>
                    <logtimefmt/>
                    <preprocessing/>
                    <jmx_endpoint/>
                    <master_item/>
                </item>
                <item>
                    <name>APC Firmware Revision</name>
                    <type>1</type>
                    <snmp_community>public</snmp_community>
                    <snmp_oid>.1.3.6.1.4.1.318.1.1.1.1.2.1.0</snmp_oid>
                    <key>apc_firmware</key>
                    <delay>60s</delay>
                    <history>90d</history>
                    <trends>0</trends>
                    <status>0</status>
                    <value_type>1</value_type>
                    <allowed_hosts/>
                    <units/>
                    <snmpv3_contextname/>
                    <snmpv3_securityname/>
                    <snmpv3_securitylevel>0</snmpv3_securitylevel>
                    <snmpv3_authprotocol>0</snmpv3_authprotocol>
                    <snmpv3_authpassphrase/>
                    <snmpv3_privprotocol>0</snmpv3_privprotocol>
                    <snmpv3_privpassphrase/>
                    <params/>
                    <ipmi_sensor/>
                    <authtype>0</authtype>
                    <username/>
                    <password/>
                    <publickey/>
                    <privatekey/>
                    <port/>
                    <description/>
                    <inventory_link>0</inventory_link>
                    <applications>
                        <application>
                            <name>Info</name>
                        </application>
                    </applications>
                    <valuemap/>
                    <logtimefmt/>
                    <preprocessing/>
                    <jmx_endpoint/>
                    <master_item/>
                </item>
                <item>
                    <name>APC Input Frequency</name>
                    <type>1</type>
                    <snmp_community>public</snmp_community>
                    <snmp_oid>.1.3.6.1.4.1.318.1.1.1.3.2.4.0</snmp_oid>
                    <key>apc_input.frequency</key>
                    <delay>30s</delay>
                    <history>90d</history>
                    <trends>365d</trends>
                    <status>0</status>
                    <value_type>3</value_type>
                    <allowed_hosts/>
                    <units>Hz</units>
                    <snmpv3_contextname/>
                    <snmpv3_securityname/>
                    <snmpv3_securitylevel>0</snmpv3_securitylevel>
                    <snmpv3_authprotocol>0</snmpv3_authprotocol>
                    <snmpv3_authpassphrase/>
                    <snmpv3_privprotocol>0</snmpv3_privprotocol>
                    <snmpv3_privpassphrase/>
                    <params/>
                    <ipmi_sensor/>
                    <authtype>0</authtype>
                    <username/>
                    <password/>
                    <publickey/>
                    <privatekey/>
                    <port/>
                    <description/>
                    <inventory_link>0</inventory_link>
                    <applications>
                        <application>
                            <name>Input</name>
                        </application>
                    </applications>
                    <valuemap/>
                    <logtimefmt/>
                    <preprocessing/>
                    <jmx_endpoint/>
                    <master_item/>
                </item>
                <item>
                    <name>APC Input Phase</name>
                    <type>1</type>
                    <snmp_community>public</snmp_community>
                    <snmp_oid>.1.3.6.1.4.1.318.1.1.1.3.1.1.0</snmp_oid>
                    <key>apc_input.phase</key>
                    <delay>30s</delay>
                    <history>90d</history>
                    <trends>365d</trends>
                    <status>0</status>
                    <value_type>3</value_type>
                    <allowed_hosts/>
                    <units/>
                    <snmpv3_contextname/>
                    <snmpv3_securityname/>
                    <snmpv3_securitylevel>0</snmpv3_securitylevel>
                    <snmpv3_authprotocol>0</snmpv3_authprotocol>
                    <snmpv3_authpassphrase/>
                    <snmpv3_privprotocol>0</snmpv3_privprotocol>
                    <snmpv3_privpassphrase/>
                    <params/>
                    <ipmi_sensor/>
                    <authtype>0</authtype>
                    <username/>
                    <password/>
                    <publickey/>
                    <privatekey/>
                    <port/>
                    <description/>
                    <inventory_link>0</inventory_link>
                    <applications>
                        <application>
                            <name>Input</name>
                        </application>
                    </applications>
                    <valuemap/>
                    <logtimefmt/>
                    <preprocessing/>
                    <jmx_endpoint/>
                    <master_item/>
                </item>
                <item>
                    <name>APC Input Voltage</name>
                    <type>1</type>
                    <snmp_community>public</snmp_community>
                    <snmp_oid>.1.3.6.1.4.1.318.1.1.1.3.2.1.0</snmp_oid>
                    <key>apc_input.volt</key>
                    <delay>30s</delay>
                    <history>90d</history>
                    <trends>365d</trends>
                    <status>0</status>
                    <value_type>0</value_type>
                    <allowed_hosts/>
                    <units>Volts</units>
                    <snmpv3_contextname/>
                    <snmpv3_securityname/>
                    <snmpv3_securitylevel>0</snmpv3_securitylevel>
                    <snmpv3_authprotocol>0</snmpv3_authprotocol>
                    <snmpv3_authpassphrase/>
                    <snmpv3_privprotocol>0</snmpv3_privprotocol>
                    <snmpv3_privpassphrase/>
                    <params/>
                    <ipmi_sensor/>
                    <authtype>0</authtype>
                    <username/>
                    <password/>
                    <publickey/>
                    <privatekey/>
                    <port/>
                    <description/>
                    <inventory_link>0</inventory_link>
                    <applications>
                        <application>
                            <name>Input</name>
                        </application>
                    </applications>
                    <valuemap/>
                    <logtimefmt/>
                    <preprocessing/>
                    <jmx_endpoint/>
                    <master_item/>
                </item>
                <item>
                    <name>APC Modell</name>
                    <type>1</type>
                    <snmp_community>public</snmp_community>
                    <snmp_oid>.1.3.6.1.4.1.318.1.1.1.1.1.1.0</snmp_oid>
                    <key>apc_model</key>
                    <delay>60s</delay>
                    <history>90d</history>
                    <trends>0</trends>
                    <status>0</status>
                    <value_type>1</value_type>
                    <allowed_hosts/>
                    <units/>
                    <snmpv3_contextname/>
                    <snmpv3_securityname/>
                    <snmpv3_securitylevel>0</snmpv3_securitylevel>
                    <snmpv3_authprotocol>0</snmpv3_authprotocol>
                    <snmpv3_authpassphrase/>
                    <snmpv3_privprotocol>0</snmpv3_privprotocol>
                    <snmpv3_privpassphrase/>
                    <params/>
                    <ipmi_sensor/>
                    <authtype>0</authtype>
                    <username/>
                    <password/>
                    <publickey/>
                    <privatekey/>
                    <port/>
                    <description>Modell der APC</description>
                    <inventory_link>0</inventory_link>
                    <applications>
                        <application>
                            <name>Info</name>
                        </application>
                    </applications>
                    <valuemap/>
                    <logtimefmt/>
                    <preprocessing/>
                    <jmx_endpoint/>
                    <master_item/>
                </item>
                <item>
                    <name>APC Output Current (Amperes)</name>
                    <type>1</type>
                    <snmp_community>public</snmp_community>
                    <snmp_oid>.1.3.6.1.4.1.318.1.1.1.4.2.4.0</snmp_oid>
                    <key>apc_output.amperes</key>
                    <delay>30s</delay>
                    <history>90d</history>
                    <trends>365d</trends>
                    <status>0</status>
                    <value_type>3</value_type>
                    <allowed_hosts/>
                    <units>Amperes</units>
                    <snmpv3_contextname/>
                    <snmpv3_securityname/>
                    <snmpv3_securitylevel>0</snmpv3_securitylevel>
                    <snmpv3_authprotocol>0</snmpv3_authprotocol>
                    <snmpv3_authpassphrase/>
                    <snmpv3_privprotocol>0</snmpv3_privprotocol>
                    <snmpv3_privpassphrase/>
                    <params/>
                    <ipmi_sensor/>
                    <authtype>0</authtype>
                    <username/>
                    <password/>
                    <publickey/>
                    <privatekey/>
                    <port/>
                    <description/>
                    <inventory_link>0</inventory_link>
                    <applications>
                        <application>
                            <name>Output</name>
                        </application>
                    </applications>
                    <valuemap/>
                    <logtimefmt/>
                    <preprocessing/>
                    <jmx_endpoint/>
                    <master_item/>
                </item>
                <item>
                    <name>APC Output Frequency</name>
                    <type>1</type>
                    <snmp_community>public</snmp_community>
                    <snmp_oid>.1.3.6.1.4.1.318.1.1.1.4.2.2.0</snmp_oid>
                    <key>apc_output.frequency</key>
                    <delay>30s</delay>
                    <history>90d</history>
                    <trends>365d</trends>
                    <status>0</status>
                    <value_type>3</value_type>
                    <allowed_hosts/>
                    <units>Hz</units>
                    <snmpv3_contextname/>
                    <snmpv3_securityname/>
                    <snmpv3_securitylevel>0</snmpv3_securitylevel>
                    <snmpv3_authprotocol>0</snmpv3_authprotocol>
                    <snmpv3_authpassphrase/>
                    <snmpv3_privprotocol>0</snmpv3_privprotocol>
                    <snmpv3_privpassphrase/>
                    <params/>
                    <ipmi_sensor/>
                    <authtype>0</authtype>
                    <username/>
                    <password/>
                    <publickey/>
                    <privatekey/>
                    <port/>
                    <description/>
                    <inventory_link>0</inventory_link>
                    <applications>
                        <application>
                            <name>Output</name>
                        </application>
                    </applications>
                    <valuemap/>
                    <logtimefmt/>
                    <preprocessing/>
                    <jmx_endpoint/>
                    <master_item/>
                </item>
                <item>
                    <name>APC Output Load</name>
                    <type>1</type>
                    <snmp_community>public</snmp_community>
                    <snmp_oid>.1.3.6.1.4.1.318.1.1.1.4.2.3.0</snmp_oid>
                    <key>apc_output.load</key>
                    <delay>30s</delay>
                    <history>90d</history>
                    <trends>365d</trends>
                    <status>0</status>
                    <value_type>3</value_type>
                    <allowed_hosts/>
                    <units>%</units>
                    <snmpv3_contextname/>
                    <snmpv3_securityname/>
                    <snmpv3_securitylevel>0</snmpv3_securitylevel>
                    <snmpv3_authprotocol>0</snmpv3_authprotocol>
                    <snmpv3_authpassphrase/>
                    <snmpv3_privprotocol>0</snmpv3_privprotocol>
                    <snmpv3_privpassphrase/>
                    <params/>
                    <ipmi_sensor/>
                    <authtype>0</authtype>
                    <username/>
                    <password/>
                    <publickey/>
                    <privatekey/>
                    <port/>
                    <description/>
                    <inventory_link>0</inventory_link>
                    <applications>
                        <application>
                            <name>Output</name>
                        </application>
                    </applications>
                    <valuemap/>
                    <logtimefmt/>
                    <preprocessing/>
                    <jmx_endpoint/>
                    <master_item/>
                </item>
                <item>
                    <name>APC Output Phase</name>
                    <type>1</type>
                    <snmp_community>public</snmp_community>
                    <snmp_oid>.1.3.6.1.4.1.318.1.1.1.4.1.2.0</snmp_oid>
                    <key>apc_output.phase</key>
                    <delay>30s</delay>
                    <history>90d</history>
                    <trends>365d</trends>
                    <status>0</status>
                    <value_type>3</value_type>
                    <allowed_hosts/>
                    <units/>
                    <snmpv3_contextname/>
                    <snmpv3_securityname/>
                    <snmpv3_securitylevel>0</snmpv3_securitylevel>
                    <snmpv3_authprotocol>0</snmpv3_authprotocol>
                    <snmpv3_authpassphrase/>
                    <snmpv3_privprotocol>0</snmpv3_privprotocol>
                    <snmpv3_privpassphrase/>
                    <params/>
                    <ipmi_sensor/>
                    <authtype>0</authtype>
                    <username/>
                    <password/>
                    <publickey/>
                    <privatekey/>
                    <port/>
                    <description/>
                    <inventory_link>0</inventory_link>
                    <applications>
                        <application>
                            <name>Output</name>
                        </application>
                    </applications>
                    <valuemap/>
                    <logtimefmt/>
                    <preprocessing/>
                    <jmx_endpoint/>
                    <master_item/>
                </item>
                <item>
                    <name>APC Output Status (basic)</name>
                    <type>1</type>
                    <snmp_community>public</snmp_community>
                    <snmp_oid>.1.3.6.1.4.1.318.1.1.1.4.1.1.0</snmp_oid>
                    <key>apc_output.status.basic</key>
                    <delay>30s</delay>
                    <history>90d</history>
                    <trends>365d</trends>
                    <status>0</status>
                    <value_type>3</value_type>
                    <allowed_hosts/>
                    <units/>
                    <snmpv3_contextname/>
                    <snmpv3_securityname/>
                    <snmpv3_securitylevel>0</snmpv3_securitylevel>
                    <snmpv3_authprotocol>0</snmpv3_authprotocol>
                    <snmpv3_authpassphrase/>
                    <snmpv3_privprotocol>0</snmpv3_privprotocol>
                    <snmpv3_privpassphrase/>
                    <params/>
                    <ipmi_sensor/>
                    <authtype>0</authtype>
                    <username/>
                    <password/>
                    <publickey/>
                    <privatekey/>
                    <port/>
                    <description/>
                    <inventory_link>0</inventory_link>
                    <applications>
                        <application>
                            <name>Output</name>
                        </application>
                    </applications>
                    <valuemap>
                        <name>APC Basic Output Status</name>
                    </valuemap>
                    <logtimefmt/>
                    <preprocessing/>
                    <jmx_endpoint/>
                    <master_item/>
                </item>
                <item>
                    <name>APC Output Voltage</name>
                    <type>1</type>
                    <snmp_community>public</snmp_community>
                    <snmp_oid>.1.3.6.1.4.1.318.1.1.1.4.2.1.0</snmp_oid>
                    <key>apc_output.volt</key>
                    <delay>30s</delay>
                    <history>90d</history>
                    <trends>365d</trends>
                    <status>0</status>
                    <value_type>0</value_type>
                    <allowed_hosts/>
                    <units>Volts</units>
                    <snmpv3_contextname/>
                    <snmpv3_securityname/>
                    <snmpv3_securitylevel>0</snmpv3_securitylevel>
                    <snmpv3_authprotocol>0</snmpv3_authprotocol>
                    <snmpv3_authpassphrase/>
                    <snmpv3_privprotocol>0</snmpv3_privprotocol>
                    <snmpv3_privpassphrase/>
                    <params/>
                    <ipmi_sensor/>
                    <authtype>0</authtype>
                    <username/>
                    <password/>
                    <publickey/>
                    <privatekey/>
                    <port/>
                    <description/>
                    <inventory_link>0</inventory_link>
                    <applications>
                        <application>
                            <name>Output</name>
                        </application>
                    </applications>
                    <valuemap/>
                    <logtimefmt/>
                    <preprocessing/>
                    <jmx_endpoint/>
                    <master_item/>
                </item>
                <item>
                    <name>APC Serial Number</name>
                    <type>1</type>
                    <snmp_community>public</snmp_community>
                    <snmp_oid>.1.3.6.1.4.1.318.1.1.1.1.2.3.0</snmp_oid>
                    <key>apc_serial</key>
                    <delay>60s</delay>
                    <history>90d</history>
                    <trends>0</trends>
                    <status>0</status>
                    <value_type>1</value_type>
                    <allowed_hosts/>
                    <units/>
                    <snmpv3_contextname/>
                    <snmpv3_securityname/>
                    <snmpv3_securitylevel>0</snmpv3_securitylevel>
                    <snmpv3_authprotocol>0</snmpv3_authprotocol>
                    <snmpv3_authpassphrase/>
                    <snmpv3_privprotocol>0</snmpv3_privprotocol>
                    <snmpv3_privpassphrase/>
                    <params/>
                    <ipmi_sensor/>
                    <authtype>0</authtype>
                    <username/>
                    <password/>
                    <publickey/>
                    <privatekey/>
                    <port/>
                    <description/>
                    <inventory_link>0</inventory_link>
                    <applications>
                        <application>
                            <name>Info</name>
                        </application>
                    </applications>
                    <valuemap/>
                    <logtimefmt/>
                    <preprocessing/>
                    <jmx_endpoint/>
                    <master_item/>
                </item>
            </items>
            <discovery_rules/>
            <httptests/>
            <macros/>
            <templates/>
            <screens/>
        </template>
    </templates>
    <triggers>
        <trigger>
            <expression>{Template APC Smart-UPS:apc_battery.replaceIndicator.last()}=2</expression>
            <recovery_mode>0</recovery_mode>
            <recovery_expression/>
            <name>Battery should be replaced</name>
            <correlation_mode>0</correlation_mode>
            <correlation_tag/>
            <url/>
            <status>0</status>
            <priority>3</priority>
            <description>Please get a new Battery and replace it as soon as possible!</description>
            <type>0</type>
            <manual_close>0</manual_close>
            <dependencies/>
            <tags/>
        </trigger>
        <trigger>
            <expression>{Template APC Smart-UPS:apc_input.frequency.last()}&lt;&gt;50</expression>
            <recovery_mode>0</recovery_mode>
            <recovery_expression/>
            <name>Frequency is not 50 Hz</name>
            <correlation_mode>0</correlation_mode>
            <correlation_tag/>
            <url/>
            <status>0</status>
            <priority>1</priority>
            <description/>
            <type>0</type>
            <manual_close>0</manual_close>
            <dependencies/>
            <tags/>
        </trigger>
        <trigger>
            <expression>{Template APC Smart-UPS:apc_input.frequency.last()}&gt;52</expression>
            <recovery_mode>0</recovery_mode>
            <recovery_expression/>
            <name>Input Fequency to high</name>
            <correlation_mode>0</correlation_mode>
            <correlation_tag/>
            <url/>
            <status>0</status>
            <priority>3</priority>
            <description/>
            <type>0</type>
            <manual_close>0</manual_close>
            <dependencies/>
            <tags/>
        </trigger>
        <trigger>
            <expression>{Template APC Smart-UPS:apc_input.frequency.last()}&lt;48</expression>
            <recovery_mode>0</recovery_mode>
            <recovery_expression/>
            <name>Input Fequency to low</name>
            <correlation_mode>0</correlation_mode>
            <correlation_tag/>
            <url/>
            <status>0</status>
            <priority>3</priority>
            <description/>
            <type>0</type>
            <manual_close>0</manual_close>
            <dependencies/>
            <tags/>
        </trigger>
        <trigger>
            <expression>{Template APC Smart-UPS:apc_output.load.last()}&gt;80</expression>
            <recovery_mode>0</recovery_mode>
            <recovery_expression/>
            <name>Load on this APC unit is to high</name>
            <correlation_mode>0</correlation_mode>
            <correlation_tag/>
            <url/>
            <status>0</status>
            <priority>2</priority>
            <description>The load on this unit is too high. Buy a stronger unit or decrease the number of devices on this UPC.</description>
            <type>0</type>
            <manual_close>0</manual_close>
            <dependencies/>
            <tags/>
        </trigger>
        <trigger>
            <expression>{Template APC Smart-UPS:apc_input.phase.last()}&lt;1</expression>
            <recovery_mode>0</recovery_mode>
            <recovery_expression/>
            <name>No Power Source</name>
            <correlation_mode>0</correlation_mode>
            <correlation_tag/>
            <url/>
            <status>0</status>
            <priority>4</priority>
            <description>The APC lost its power source.</description>
            <type>0</type>
            <manual_close>0</manual_close>
            <dependencies/>
            <tags/>
        </trigger>
        <trigger>
            <expression>{Template APC Smart-UPS:apc_battery.time.remaining.last()}&lt;5m</expression>
            <recovery_mode>0</recovery_mode>
            <recovery_expression/>
            <name>Remaining Time on Battery is lower than 5 Minutes</name>
            <correlation_mode>0</correlation_mode>
            <correlation_tag/>
            <url/>
            <status>0</status>
            <priority>5</priority>
            <description/>
            <type>0</type>
            <manual_close>0</manual_close>
            <dependencies/>
            <tags/>
        </trigger>
        <trigger>
            <expression>{Template APC Smart-UPS:apc_diagnostics.testResults.last()}=2</expression>
            <recovery_mode>0</recovery_mode>
            <recovery_expression/>
            <name>Test Failed</name>
            <correlation_mode>0</correlation_mode>
            <correlation_tag/>
            <url/>
            <status>0</status>
            <priority>3</priority>
            <description>The diagnostic Test failed.</description>
            <type>0</type>
            <manual_close>0</manual_close>
            <dependencies/>
            <tags/>
        </trigger>
        <trigger>
            <expression>{Template APC Smart-UPS:apc_battery.capacity.last()}&lt;10</expression>
            <recovery_mode>1</recovery_mode>
            <recovery_expression>{Template APC Smart-UPS:apc_battery.capacity.last()}&gt;10</recovery_expression>
            <name>UPS Capacity lower than 10 Percent</name>
            <correlation_mode>0</correlation_mode>
            <correlation_tag/>
            <url/>
            <status>0</status>
            <priority>5</priority>
            <description>The Battery Capacity is lower than 10%. Check the Power source.</description>
            <type>0</type>
            <manual_close>0</manual_close>
            <dependencies/>
            <tags/>
        </trigger>
        <trigger>
            <expression>{Template APC Smart-UPS:apc_battery.capacity.last()}&lt;20</expression>
            <recovery_mode>1</recovery_mode>
            <recovery_expression>{Template APC Smart-UPS:apc_battery.capacity.last()}&gt;20</recovery_expression>
            <name>UPS Capacity lower than 20 Percent</name>
            <correlation_mode>0</correlation_mode>
            <correlation_tag/>
            <url/>
            <status>0</status>
            <priority>4</priority>
            <description>The Battery Capacity is lower than 20%. Check the Power source.</description>
            <type>0</type>
            <manual_close>0</manual_close>
            <dependencies/>
            <tags/>
        </trigger>
        <trigger>
            <expression>{Template APC Smart-UPS:apc_battery.capacity.last()}&lt;30</expression>
            <recovery_mode>1</recovery_mode>
            <recovery_expression>{Template APC Smart-UPS:apc_battery.capacity.last()}&gt;30</recovery_expression>
            <name>UPS Capacity lower than 30 Percent</name>
            <correlation_mode>0</correlation_mode>
            <correlation_tag/>
            <url/>
            <status>0</status>
            <priority>3</priority>
            <description>The Battery Capacity is lower than 30%. Check the Power source.</description>
            <type>0</type>
            <manual_close>0</manual_close>
            <dependencies/>
            <tags/>
        </trigger>
        <trigger>
            <expression>{Template APC Smart-UPS:apc_battery.capacity.last()}&lt;50</expression>
            <recovery_mode>1</recovery_mode>
            <recovery_expression>{Template APC Smart-UPS:apc_battery.capacity.last()}&gt;50</recovery_expression>
            <name>UPS Capacity lower than 50 Percent</name>
            <correlation_mode>0</correlation_mode>
            <correlation_tag/>
            <url/>
            <status>0</status>
            <priority>3</priority>
            <description>The Battery Capacity is lower than 50%. Check the Power source.</description>
            <type>0</type>
            <manual_close>0</manual_close>
            <dependencies/>
            <tags/>
        </trigger>
        <trigger>
            <expression>{Template APC Smart-UPS:apc_battery.capacity.last()}&lt;50</expression>
            <recovery_mode>1</recovery_mode>
            <recovery_expression>{Template APC Smart-UPS:apc_battery.capacity.last()}&gt;70</recovery_expression>
            <name>UPS Capacity lower than 70 Percent</name>
            <correlation_mode>0</correlation_mode>
            <correlation_tag/>
            <url/>
            <status>0</status>
            <priority>2</priority>
            <description>The Battery Capacity is lower than 70%. Check the Power source.</description>
            <type>0</type>
            <manual_close>0</manual_close>
            <dependencies/>
            <tags/>
        </trigger>
        <trigger>
            <expression>{Template APC Smart-UPS:apc_battery.capacity.last()}&lt;90</expression>
            <recovery_mode>1</recovery_mode>
            <recovery_expression>{Template APC Smart-UPS:apc_battery.capacity.last()}&gt;90</recovery_expression>
            <name>UPS Capacity lower than 90 Percent</name>
            <correlation_mode>0</correlation_mode>
            <correlation_tag/>
            <url/>
            <status>0</status>
            <priority>1</priority>
            <description>The Battery Capacity is lower than 90%. Run Diagnostics.</description>
            <type>0</type>
            <manual_close>0</manual_close>
            <dependencies/>
            <tags/>
        </trigger>
    </triggers>
    <graphs>
        <graph>
            <name>Frequency</name>
            <width>900</width>
            <height>200</height>
            <yaxismin>0.0000</yaxismin>
            <yaxismax>100.0000</yaxismax>
            <show_work_period>1</show_work_period>
            <show_triggers>1</show_triggers>
            <type>0</type>
            <show_legend>1</show_legend>
            <show_3d>0</show_3d>
            <percent_left>0.0000</percent_left>
            <percent_right>0.0000</percent_right>
            <ymin_type_1>0</ymin_type_1>
            <ymax_type_1>0</ymax_type_1>
            <ymin_item_1>0</ymin_item_1>
            <ymax_item_1>0</ymax_item_1>
            <graph_items>
                <graph_item>
                    <sortorder>0</sortorder>
                    <drawtype>0</drawtype>
                    <color>1A7C11</color>
                    <yaxisside>0</yaxisside>
                    <calc_fnc>2</calc_fnc>
                    <type>0</type>
                    <item>
                        <host>Template APC Smart-UPS</host>
                        <key>apc_input.frequency</key>
                    </item>
                </graph_item>
                <graph_item>
                    <sortorder>1</sortorder>
                    <drawtype>0</drawtype>
                    <color>F63100</color>
                    <yaxisside>0</yaxisside>
                    <calc_fnc>2</calc_fnc>
                    <type>0</type>
                    <item>
                        <host>Template APC Smart-UPS</host>
                        <key>apc_output.frequency</key>
                    </item>
                </graph_item>
            </graph_items>
        </graph>
    </graphs>
    <value_maps>
        <value_map>
            <name>APC Basic Output Status</name>
            <mappings>
                <mapping>
                    <value>1</value>
                    <newvalue>unknown</newvalue>
                </mapping>
                <mapping>
                    <value>2</value>
                    <newvalue>onLine</newvalue>
                </mapping>
                <mapping>
                    <value>3</value>
                    <newvalue>onBattery</newvalue>
                </mapping>
                <mapping>
                    <value>4</value>
                    <newvalue>onSmartBoost</newvalue>
                </mapping>
                <mapping>
                    <value>5</value>
                    <newvalue>timedSleeping</newvalue>
                </mapping>
                <mapping>
                    <value>6</value>
                    <newvalue>softwareBypass</newvalue>
                </mapping>
                <mapping>
                    <value>7</value>
                    <newvalue>off</newvalue>
                </mapping>
                <mapping>
                    <value>8</value>
                    <newvalue>rebooting</newvalue>
                </mapping>
                <mapping>
                    <value>9</value>
                    <newvalue>switchedBypass</newvalue>
                </mapping>
                <mapping>
                    <value>10</value>
                    <newvalue>hardwareFailureBypass</newvalue>
                </mapping>
                <mapping>
                    <value>11</value>
                    <newvalue>sleepingUntilPowerReturn</newvalue>
                </mapping>
                <mapping>
                    <value>12</value>
                    <newvalue>onSmartTrim</newvalue>
                </mapping>
                <mapping>
                    <value>13</value>
                    <newvalue>ecoMode</newvalue>
                </mapping>
                <mapping>
                    <value>14</value>
                    <newvalue>hotStandby</newvalue>
                </mapping>
                <mapping>
                    <value>15</value>
                    <newvalue>onBatteryTest</newvalue>
                </mapping>
                <mapping>
                    <value>16</value>
                    <newvalue>emergencyStaticBypass</newvalue>
                </mapping>
                <mapping>
                    <value>17</value>
                    <newvalue>staticBypassStandby</newvalue>
                </mapping>
                <mapping>
                    <value>18</value>
                    <newvalue>powerSavingMode</newvalue>
                </mapping>
                <mapping>
                    <value>19</value>
                    <newvalue>spotMode</newvalue>
                </mapping>
                <mapping>
                    <value>20</value>
                    <newvalue>eConversion</newvalue>
                </mapping>
                <mapping>
                    <value>21</value>
                    <newvalue>chargerSpotmode</newvalue>
                </mapping>
                <mapping>
                    <value>22</value>
                    <newvalue>inverterSpotmode</newvalue>
                </mapping>
            </mappings>
        </value_map>
        <value_map>
            <name>APC Battery Replacement Indicator</name>
            <mappings>
                <mapping>
                    <value>1</value>
                    <newvalue>noBatteryNeedsReplacing</newvalue>
                </mapping>
                <mapping>
                    <value>2</value>
                    <newvalue>batteryNeedsReplacing</newvalue>
                </mapping>
            </mappings>
        </value_map>
        <value_map>
            <name>APC Battery Status</name>
            <mappings>
                <mapping>
                    <value>1</value>
                    <newvalue>unknown</newvalue>
                </mapping>
                <mapping>
                    <value>2</value>
                    <newvalue>batteryNormal</newvalue>
                </mapping>
                <mapping>
                    <value>3</value>
                    <newvalue>batteryLow</newvalue>
                </mapping>
            </mappings>
        </value_map>
        <value_map>
            <name>APC Diagnostic Result</name>
            <mappings>
                <mapping>
                    <value>1</value>
                    <newvalue>ok</newvalue>
                </mapping>
                <mapping>
                    <value>2</value>
                    <newvalue>failed</newvalue>
                </mapping>
                <mapping>
                    <value>3</value>
                    <newvalue>invalidTest</newvalue>
                </mapping>
                <mapping>
                    <value>4</value>
                    <newvalue>testInProgress</newvalue>
                </mapping>
            </mappings>
        </value_map>
    </value_maps>
</zabbix_export>
